This guide describes the current state of knowledge of the relationship between tank rupture and such variables as arc energy level, hydraulic pressures and tank pressure withstand. Also described are various measures that transformer users and manufacturers may take in system design, product design, monitoring devices, signaling devices and fluid choices that can help to mitigate tank rupture.This guide describes measures that may be taken to help mitigate tank rupture of energized liquid-immersed power transformers and reactors due to internal electrical faults. This guide does not cover the release of oil or oil mist due to failure of the following components: load tap changer compartments, bushings and their turrets, conservator tank, piping, valves, pumps and radiators.
Get Involved In The Development Of This Standard
Contact the IEEE-SA Liaison Simply click here to voice your interest. Erin Spiewak Learn More About Standards ParticipationAnyone can participate, there are a variety of programs and services to
facilitate the involvement of industry and the public. More Become a Member and Ballot on this StandardMembership empowers you to participate & lead in the development of
standards. Tell Me More