This guide covers the technical requirements for the design, fabrication, testing, installation, and in-service performance of gas-insulated substations(GIS). In line with the user functional one-line diagram, the supplier should furnish all components of the GIS such as circuit breakers(CB), disconnect switches(DS), maintenance ground switches (MGS), fast-acting ground switches(FGS), voltage transformers(VT), current transformers(CT), SF6-to-air bushings, SF6-to-cable terminations, surge arresters, all the necessary interconnecting housings, control cabinets, density monitors, interconnecting cables, SF6 gas for initial filling etc. All equipment and material shall be prefabricated, factory assembled, tested and shipped in largest practical assemblies. Assembled equipment should be capable of withstanding electrical, mechanical, and thermal ratings of the specified system for indoor or outdoor istallation. Optimized arrangements should allow reduced installation time, ease of operation, minimize maintenance and repair costs with provision for future extension. Users should identify any limitations in space and accessibility constraints. Life-cycle costs are considered by the users during evaluation of the proposals.
Get Involved In The Development Of This Standard
Contact the IEEE-SA Liaison Simply click here to voice your interest. Erin Spiewak Learn More About Standards ParticipationAnyone can participate, there are a variety of programs and services to
facilitate the involvement of industry and the public. More Become a Member and Ballot on this StandardMembership empowers you to participate & lead in the development of
standards. Tell Me More