This standard is intended for use as a basis for establishing the performance, electrical and mechanical interchangeability, and safety of the equipment covered, and to assist in the proper selection of such equipment.This standard covers certain electrical, dimensional, and mechanical characteristics and takes into consideration certain safety features of three-phase, 60 Hz, liquid-immersed, self-cooled, submersible transformers with separable insulated high-voltage connectors. These transformers are rated 3750 kVA and smaller with high voltages of 34 500 GrdY/19 920 V and below and with low voltages of 600 V and below. These transformers are generally used for step-down purposes from an underground primary cable supply. These transformers are typically installed in an enclosure below ground level, operated from above and suitable for continuous submerged operation.
Get Involved In The Development Of This Standard
Contact the IEEE-SA Liaison Simply click here to voice your interest. Erin Spiewak
Learn More About Standards ParticipationAnyone can participate, there are a variety of programs and services to
facilitate the involvement of industry and the public. More
Become a Member and Ballot on this StandardMembership empowers you to participate & lead in the development of
standards. Tell Me More