This document gives the recommended practices for designing and installing the interfaces between an existing Gas-Insulated Substations (GIS) equipment and a new GIS equipment that is added at a later date, and may be of different design and of different manufacturer. The recommended practices apply for GIS rated above 52kV. They also include the interfaces between Gas-Insulated Line (GIL) equipment and Gas-Insulated Substations (GIS) equipment rated above 52kV.
Get Involved In The Development Of This Standard
Contact the IEEE-SA Liaison Simply click here to voice your interest. Erin Spiewak Learn More About Standards ParticipationAnyone can participate, there are a variety of programs and services to
facilitate the involvement of industry and the public. More Become a Member and Ballot on this StandardMembership empowers you to participate & lead in the development of
standards. Tell Me More