Recommendations for operation and maintenance of dry-type distribution and power transformers are provided.
Working Group Details
Other Activities From This Working Group
Current projects that have been authorized by the IEEE SA Standards Board to develop a standard.
Recommended Practice for Installation, Application, Operation, and Maintenance of Dry-Type Distribution and Power Transformers
This recommended practice describes general recommendations for the installation, application, operation, and maintenance of all single and polyphase ventilated, non-ventilated, and sealed dry-type distribution and power transformers or autotransformers, including those with solid-cast and/or resin encapsulated windings except transformers described as exceptions in IEEE Std C57.12.01. nnNOTE–Where IEEE standards do not exist for the transformers mentioned above or for other special transformers, this standard may be applicable as a whole or in parts subject to agreement between the parties responsible for the application and for the design of the transformer.
Standards approved by the IEEE SA Standards Board that are within the 10-year lifecycle.
No Active Standards
These standards have been replaced with a revised version of the standard, or by a compilation of the original active standard and all its existing amendments, corrigenda, and errata.
IEEE Recommended Practice for Installation, Application, Operation, and Maintenance of Dry-Type General Purpose Distribution and Power Transformers
The application, installation, operation, and maintenance of single- and polyphase dry-type general purpose, distribution, power, and autotransformers are covered. The following types are included: ventilated, indoor and outdoor, self- or forced-air cooled; nonventilated, indoor and outdoor, self- or forced-air cooled; and sealed, indoor and outdoor, self-cooled. Instrument transformers, step voltage and induction-voltage regulators, arc furnace transformers, rectifier transformers, and specialty transformers are not covered.
These standards have been removed from active status through a ballot where the standard is made inactive as a consensus decision of a balloting group.
No Inactive-Withdrawn Standards
These standards are removed from active status through an administrative process for standards that have not undergone a revision process within 10 years.
No Inactive-Reserved Standards