Insulating oil contained in equipment such as transformers, circuit-breaking devices, regulators, series and shunt reactors, as received from the manufacturer and as filled at the installation site but prior to service operation, should exhibit certain properties in order to insure satisfactory performance. I t is expected that oil contained in equipment as received from the manufacturer when properly sampled from such equipment usually exhibits characteristics slightly different from those obtained from new oil, which has not been in contact with apparatus constructional materials. Additionally, certain essential properties of insulating oil, used in transformers and circuit-breaking devices, must be retained in service if the oil is to perform its multiple role of electrical-insulating, arc-quenching, and heat-transferring agent reliably. It must have adequate dielectric strength to withstand the electric stresses imposed in service. I t must retain a sufficiently low viscosity so that its ability to circulate and transfer heat is not impaired. It must pour readily at low temperatures and have high flash point and fire point for safety. Its dielectric losses should not become excessive. It should not be allowed to become so deteriorated or contaminated that it adversely affects other materials in the apparatus, nor should deterioration products sludge it sufficiently to impair its circulation through cooling ducts. This Guide attempts to assist the power equipment operator in evaluating oil received in equipment and as filled at the installation site and to assist also in his efforts to maintain his oil in serviceable condition. It recommends and standardizes oil test and ^valuation procedures, methods of reconditioning and declaiming oil when necessary, and routines for restoring oxidation resistance by additions of inhibitors
Working Group Details
Other Activities From This Working Group
Current projects that have been authorized by the IEEE SA Standards Board to develop a standard.
No Active Projects
Standards approved by the IEEE SA Standards Board that are within the 10-year lifecycle.
No Active Standards
These standards have been replaced with a revised version of the standard, or by a compilation of the original active standard and all its existing amendments, corrigenda, and errata.
No Superseded Standards
These standards have been removed from active status through a ballot where the standard is made inactive as a consensus decision of a balloting group.
No Inactive-Withdrawn Standards
These standards are removed from active status through an administrative process for standards that have not undergone a revision process within 10 years.
No Inactive-Reserved Standards