This guide covers general recommendations for the operation and maintenance of indoor, openly-ventilated, dry type distribution and power transformers with Class B insulation in ratings above 50 kva and above 600 volts, cooled by natural draft or forced draft. The successful operation of these transformers is dependent on proper installation, loading and maintenance as well as on proper design and manufacture. As with all electric apparatus, neglect of certain fundamental requirements may lead to serious trouble, if not to the loss of the equipment. For this reason, a wide distribution of information in regard to the care of dry type transformers is important, and these brief instructions are published for that purpose. In addition to the use of this guide, the manufacturer should be consulted for specific recommendations on special conditions. Also reference may be made to other publications, some of which are listed in the Appendix.
- Inactive-Withdrawn Standard
Working Group Details
Other Activities From This Working Group
Current projects that have been authorized by the IEEE SA Standards Board to develop a standard.
No Active Projects
Standards approved by the IEEE SA Standards Board that are within the 10-year lifecycle.
No Active Standards
These standards have been replaced with a revised version of the standard, or by a compilation of the original active standard and all its existing amendments, corrigenda, and errata.
No Superseded Standards
These standards have been removed from active status through a ballot where the standard is made inactive as a consensus decision of a balloting group.
No Inactive-Withdrawn Standards
These standards are removed from active status through an administrative process for standards that have not undergone a revision process within 10 years.
No Inactive-Reserved Standards