Looking at the problem from an overall standpoint, the grounding of the system would in most cases be done by making a metallic connection direct or through an impedance between transformer or generator neutrals and the building grounding system which is described in Chapter II. The grounding system described in Chapter II in turn is connected to earth through the system of ground rods and water pipes described in Chapter IV. The protective systems discussed for static and lightning protection in Chapter III would likewise be connected to the ground rods and water pipe system as outlined in Chapter IV.
- Superseded Standard
- Board Approval
Working Group Details
Other Activities From This Working Group
Current projects that have been authorized by the IEEE SA Standards Board to develop a standard.
No Active Projects
Standards approved by the IEEE SA Standards Board that are within the 10-year lifecycle.
No Active Standards
These standards have been replaced with a revised version of the standard, or by a compilation of the original active standard and all its existing amendments, corrigenda, and errata.
No Superseded Standards
These standards have been removed from active status through a ballot where the standard is made inactive as a consensus decision of a balloting group.
No Inactive-Withdrawn Standards
These standards are removed from active status through an administrative process for standards that have not undergone a revision process within 10 years.
No Inactive-Reserved Standards