Working Group Details
Dist-WGC57.15 - Distribution - Step-Voltage Regulator Working Group
|Working Group Chair||
|IEEE Program Manager|
Electrical, mechanical, and safety requirements of oil-filled, single- and three-phase voltage regulators not exceeding regulation of 2500 kVA (for three-phase units) or 833 kVA (for single-phase units) are covered.
Description of design types, tables of 50 Hz and 60 Hz ratings, supplementary ratings, construction, and available accessories are provided. Methods for performing routine and design tests applicable to liquid-immersed single and three-phase step-voltage regulators are described. Winding resistance measurements, polarity tests, insulation power factor and resistance tests, ratio tests, no load loss and excitation current measurements, impedance and load loss measurements, dielectric tests, temperature tests, routine and design impulse tests, short-circuit tests, control tests, calculated data, and certified test data are covered.
C57.15-2017 - IEEE/IEC International Standard- Power transformers - Part 21: Standard requirements, terminology, and test code for step-voltage regulators
This document describes electrical, mechanical and test requirements of liquid-immersed, single- and three-phase, 50 Hz and 60 Hz, self and forced-air cooled, distribution, overhead and substation, step-voltage regulators, 1 000 kVA (single-phase units) or 3 000 kVA (threephase units) and smaller, 34 500 volts and below (2 400 V minimum) and their associated controls. Requirements, references and definitions relevant to eithere IEC or IEEE contexts are given and their use is described in Clause 4.