Certain electrical, dimensional, and mechanical characteristics are covered in this standard, and certain safety features of single-phase, 60-Hz, mineral-oil-immersed, self-cooled, pad-mounted, compartmental-type distribution transformers are taken into consideration. These
transformers are rated 250 kVA and smaller with high voltages of 34 500 GrdY/19 920 V and below and with low voltages of 480/240 V and below. These transformers are generally used for step-down purposes from an underground primary cable supply. The connector, bushing, and
terminal arrangements for radial or loop feed systems are covered in this standard. The electrical and mechanical requirements of any accessory devices that may be supplied with the transformer are not covered in this standard.