Working Group Details
HVS-WG_C37.30.1 - HVS - Standard Requirements For High Voltage Air Switches And Interrupting Switches for Alternating Current, Rated Above 1,000 Volts
|Working Group Chair||
|IEEE Program Manager|
This standard covers preferred ratings; construction and testing requirements; and application, loading, installation, operation, and maintenance guidelines for all high-voltage enclosed and nonenclosed, indoor and outdoor air switches rated in excess of 1000 V. This includes such switch types as disconnect, horngap, fault-initiation, and ground for manual or power operation. The following switch types are not covered by this standard: interrupter switches, distribution cutouts fitted with disconnecting blades, and switches used in metal-enclosed and pad-mounted switchgear. This standard also does not apply to load-break separable insulated connectors, circuit breakers, circuit switchers, or reclosers.
Required ratings, construction requirements, design test requirements, applications, and suggested practices for all high-voltage enclosed indoor and outdoor and nonenclosed indoor and outdoor switches rated above 1000 V are specified. This includes ratings and requirements for such switches as disconnecting, selector, horn-gap, and grounding for manual and power operation, except for interrupter switches, distribution-enclosed single-pole air switches, and distribution cutouts fitted with disconnecting blades. Supersedes IEEE Std C37.30, IEEE Std C37.32, IEEE Std C37.34, IEEE Std C37.35, IEEE Std C37.36b, IEEE Std C37.37