This recommended practice provides procedures that can be used to optimize the reliability and service life of nickel-cadmium batteries in stationary applications.This document provides recommendations for installation design and procedures for installation, maintenance, and testing of vented nickel-cadmium batteries (including partially recombinant types) used for standby operation in stationary applications. This recommended practice also provides guidance for determining when these batteries should be replaced. Separate recommendations are provided for renewable energy systems (e.g., wind turbines and photovoltaic systems), which may provide only partial or intermittent charging. Sizing, qualification, and other battery types, including sealed nickel-cadmium, are also beyond the scope of this document. This recommended practice does not include any other component of the dc system, nor does it include inspection and testing of the overall dc system. Preoperational and periodic dc system tests of chargers and other dc components may require that the battery be connected to the system. Details for these tests will depend on the requirements of the dc system and are beyond the scope of this document.
Get Involved In The Development Of This Standard
Contact the IEEE-SA Liaison Simply click here to voice your interest. Malia Zaman Learn More About Standards ParticipationAnyone can participate, there are a variety of programs and services to
facilitate the involvement of industry and the public. More Become a Member and Ballot on this StandardMembership empowers you to participate & lead in the development of
standards. Tell Me More