Description: This guide describes field test methods that assure that current transformers are connected properly, are of marked ratio and polarity, and are in a condition to perform as designed both initially and after having been in service for a period of time.
Get This Standard
Buy Purchase a copy of this standard Buy
Buy VuSpec CD ROM This standard can be purchased as part of the following VuSpect CDs:
- IEEE Power Switchgear, Substations & Relays Standards Collection Buy
- IEEE Power Distribution & Regulating Transformers Collection: VuSpec™ Buy
- IEEE Power Systems Relays Standards Collection Buy
Access with Subscription Standards Online subscribers can access this standard in IEEE Xplore Digital Library. Access Learn More