Description: Protective devices, such as relays and fuses, have well-defined operating characteristics that relate fault magnitude to operating time. It is desirable that these characteristic curves be coordinated with comparable curves applicable to dry-type transformers that relate duration and fault magnitude to withstand capability. This guide sets forth recommendations believed essential for the application of overcurrent protective devices applied to limit the exposure time of dry-type transformers to short-circuit currents. This guide is not intended to imply overload capability.
Sponsor: IEEE Power and Energy Society
Get This Standard
Buy Purchase a copy of this standard Buy
Access with Subscription Standards Online subscribers can access this standard in IEEE Xplore Digital Library. Access Learn More