Description: Recommendations regarding oil tests and evaluation procedures are made in this guide; references are made to methods of reconditioning and reclaiming conventional petroleum (mineral) dielectric insulating oils; the levels at which these methods become necessary; and the routines for restoring oxidation resistance, where required, by the addition of oxidation inhibitors. The intent is to assist the power equipment operator in evaluating the serviceability of oil received in equipment, oil as received from the supplier for filling new equipment at the installation site, and oil as processed into such equipment; and to assist the operator in maintaining oil in serviceable condition. The mineral oil covered is used in transformers, reactors, circuit breakers, load tap changers, and voltage regulators.
Get This Standard
Buy Purchase a copy of this standard Buy
Buy VuSpec CD ROM This standard can be purchased as part of the following VuSpect CD:
- IEEE Power Distribution & Regulating Transformers Collection: VuSpec™ Buy
Access with Subscription Standards Online subscribers can access this standard in IEEE Xplore Digital Library. Access Learn More