Description: A step-by-step process for selecting an appropriate termination that is commensurate with a particular shielded power cable design is provided in this guide. Over the years, shielded power cables have been developed that employ many different insulating materials and many different shielding systems, such that, there are numerous issues to consider when selecting a termination for a particular cable design. Over the same period of time, many different termination methods and designs have been developed that serve the same purpose, but employ different application methodologies. This guide does not attempt to cover every cable and termination design, and is generally restricted to single conductor underground residential distribution (URD) and shielded power cable that have a voltage rating from 5 kV – 46 kV, which includes some industrial cables. By nature, the terminations referred to in this guide are considered to be “live front,” in that the terminations comprise a transition from a shielded power cable system to an energized component or bus that is either bare or simply covered.
Oversight Committee: PE/IC - Insulated Conductors
Sponsor: IEEE Power and Energy Society
Get This Standard
Buy Purchase a copy of this standard Buy
Access with Subscription Standards Online subscribers can access this standard in IEEE Xplore Digital Library. Access Learn More