IEEE Standards Interpretation for IEEE Std 383™-1974 IEEE Standard for Type Test of Class 1E Electric Cables, Field Splices and Connections for Nuclear Power Generating Stations
Copyright © 2005 by the Institute of Electrical and Electronics Engineers, Inc. 3 Park Avenue New York, New York 10016-5997 USA All Rights Reserved.
Interpretations are issued to explain and clarify the intent of a standard and do not constitute an alteration to the original standard. In addition, interpretations are not intended to supply consulting information. Permission is hereby granted to download and print one copy of this document. Individuals seeking permission to reproduce and/or distribute this document in its entirety or portions of this document must contact the IEEE Standards Department for the appropriate license. Use of the information contained in this document is at your own risk.
IEEE Standards Department Copyrights and Permissions 445 Hoes Lane, Piscataway, New Jersey 08855-1331, USA
Interpretation Request #1
Relevant Clause: Subclause 2.3.2 (Aging Data) to 2.4.4 Topic: Long term physical aging properties
Which way should the test be conducted? Should [we] age the complete cable sample or should the insulated conductors be taken out of the cable? In general, the cables selected as samples for qualification must be representative of the family of cables being qualified and of installed configurations. This may require that individual insulated conductors, multi-conductor jacketed cables or jacketed single conductor cables be part of the test program. Both aged and unaged samples should be selected. These samples will be required to be exposed to thermal aging, radiation aging, DBE conditions, and to pass post DBE tests.
Long term physical aging is thermal aging, and aging times should be determined based on the material properties utilized in the construction of the cable. Accelerated aging may need to be part of the test program, if naturally aged samples cannot be obtained. If accelerated aging is employed, the Arrhenius technique should be used to establish aging times and temperatures. It may be necessary, and desirable, to perform accelerated tests on both the completed cable and individual insulated conductors. The insulated conductors will need to be aged to their end of life condition. Aging of the completed cable is particularly important if the cable has a bonded jacket.
Interpretation Request #2
Relevant Clause: Subclause 2.4.2 to 2.4.4 Topic: Radiation Exposure - Total
Cable or insulated conductor from cable?
Whatever samples are selected for thermal aging should continue through the radiation exposure and the remainder of the test program.
Interpretation Request #3
Relevant Clause: Subclause 126.96.36.199
The word "Cable" is appearing. Does it mean the cable is subjected to LOCA?
Yes, the cable (test samples) are subjected to LOCA conditions.
Interpretation Request #4
For radiation exposure and LOCA rest whether the specimens are insulated cores taken out of the cable or the complete cable is subjected for the test of radiation exposure. What is the practice please?
The Nuclear Power Engineering Committee (NPEC) is unclear what the specific question is. NPEC can interpret the question one of two ways.
Should the copper conductor be removed leaving a hollow insulated tube (core) or should the conductors remain within the insulation for the test? The cable should be tested with the conductor in the cable or insulated conductor. If the conductor is removed from the cable, it will no be possible to demonstrate the cable will function electrically.
Should the test samples (insulated single conductors, complete multi-conductor cable, jacketed single conductor cable, etc.) be exposed to radiation and LOCA conditions of the test? Whatever samples are selected for thermal aging should continue the radiation exposure and the remainder of the test.
Interpretation Request #5
Does the word “Specimen” in Cl 2.4.4 refer to the cable or conductors removed from the cable?
The specimens are the samples that have gone through the test program. These could be both individual insulated conductors and/or completed cables.
Are there additional references to any International standards for carrying out these tests for Class 1E cables?
NPEC is not aware of a similar International standard, hence no guidance is provided in this area.