IEEE Standards Interpretation for IEEE Std 344™-1987 IEEE Recommended Practice for Seismic Qualification of Class 1E Equipment for Nuclear Power Generating Stations
Copyright © 2002 by the Institute of Electrical and Electronics Engineers, Inc. 3 Park Avenue New York, New York 10016-5997 USA All Rights Reserved.
Interpretations are issued to explain and clarify the intent of a standard and do not constitute an alteration to the original standard. In addition, interpretations are not intended to supply consulting information. Permission is hereby granted to download and print one copy of this document. Individuals seeking permission to reproduce and/or distribute this document in its entirety or portions of this document must contact the IEEE Standards Department for the appropriate license. Use of the information contained in this document is at your own risk.
IEEE Standards Department Copyrights and Permissions 445 Hoes Lane, Piscataway, New Jersey 08855-1331, USA
Interpretation Request #1
Topic: Design Life of a Nuclear Power Plant (Equipment Qualification Department) Relevant Clause: Subclause 22.214.171.124
In 126.96.36.199 of IEEE Std 344 -1987, 188.8.131.52, Seismic Aging (OBE), there is following sentence:
"The number of OBE shall be justified for each site or shall produce the equivalent effect of five OBE."
Please interpret the above sentence as to whether 5 OBEs could be applied when design life of a nuclear power plant, especially the equipment qualification department, is increased from 40 to 60 years.
IEEE Std 344 states only that the number of OBEs should be justified or shall produce the equivalent of 5 OBEs. The number of OBE occurrences for a specified design life of the nuclear power plant is not specified. The OBE tests preceding the SSE are performed to seismically age (fatigue) the test specimen. Determination of how many OBE occurrences are appropriate for a particular site over its design life is the responsibility of the Owner or the Owner's designee, subject to regulatory agency approval.