This standard specifies design test requirements for high-voltage (above 1000 V) fuses and accessories for use on ac electrical distribution systems. Devices having a rated maximum voltage up to 170 kV are covered. The devices to which this standard applies are as follows: a)Expulsion fuses (including fuse cutouts) b)Current-limiting fuses c)Items a) and b) used in fuse enclosure packages d)Fuse supports of the type intended for use with fuses and fuse disconnecting switches e)Disconnecting devices (fuse disconnecting switches, disconnecting switches, and disconnecting cutouts) created by the use of a removable fuse unit or switch blade in a fuse support f)Expulsion, current-limiting, and combination types of external capacitor fuses used with a capacitor unit, a group of units, or capacitor banks g)Backup current-limiting fuses ("e;motor-starter fuses"e;) used in conjunction with high-voltage motor starters h)Fuse links when used exclusively with expulsion fuses, and fuse disconnecting switches i)Items a) through f) having integral load-break means This standard may also be used as a basis for testing other devices that are similar to the devices listed in the scope. In addition, the parts relating to expulsion fuses may, where applicable, be used for non-expulsion fuses in which the interruption process waits for a natural current zero to clear the circuit. The manufacturer and the user should agree on any specifications or tests performed for such devices.
Get Involved In The Development Of This Standard
Contact the IEEE-SA Liaison Simply click here to voice your interest. Erin Spiewak Learn More About Standards ParticipationAnyone can participate, there are a variety of programs and services to
facilitate the involvement of industry and the public. More Become a Member and Ballot on this StandardMembership empowers you to participate & lead in the development of
standards. Tell Me More