This standard provides a test procedure for determining the ampacity derating factor in the following cable installation configurations: -- Block-out or sleeve type cable penetration fire stops -- Conduits covered with a protective material -- Tray covered with a protective material -- Cable directly covered or coated with a fire-retardant material -- Free-air drops enclosed with a protective material The standard is applicable to cables installed and sized to IEEE Std 835 for conduits and free-air drops, and NEMA WC51/ICEA P-54-440 for cable tray. IEEE Std 835 does provide ampacities for cables in a tray with a fixed spacing and may be used for cable penetration fire stop configurations only. This standard does not endorse the use of or provide application guidance for the installation of cable penetration fire stops and fire-protective materials. Cable designs are available that can withstand and remain functional during direct exposure to a fire. The user should refer to IEEE Std 634 for the qualification requirements of cable penetration fire stops.
Get Involved In The Development Of This Standard
Contact the IEEE-SA Liaison Simply click here to voice your interest. Malia Zaman Learn More About Standards ParticipationAnyone can participate, there are a variety of programs and services to
facilitate the involvement of industry and the public. More Become a Member and Ballot on this StandardMembership empowers you to participate & lead in the development of
standards. Tell Me More